At present,floating coil heat exchanger is the new product improved on the basis of former products. Now it has been the Generation VI Product by our continued optimizing and improving. Because we use the smaller heat transfer component, it has tight structure and reasonable layout The moreover, the decrease of outer size has solved the problem short flow caused by uneven flow velocity on the circular cross-section of former shell side, therefore its potential functions of high heat transfer coefficient K and stable thermostatic water supply can be brought into to the full play.
The floating coil heat exchanger can be widely used in the supply system of heating,air conditioning and domestic hot water in the industrial and civil buildings just like hotels,restaurants,organs,schools,hospitals,laundries,factories and so on.
1. Intensified Heat Transfer The spiral copper coil pipe is fixed by the cantilever construction. As the hot mediators(saturation steam or high-temperature water)pass the pipe, The pipe’s high-speed round trip motion causes perturbation motion of the water around the heat exchanger tubes forcedly, and this increases the heat transfer coefficient “K”, reduces the fluid‘s thermal resistance on the tubes outer wall “l/a0”, and enhances the total heat transfer coefficient. 2. Less solid fouling Because of the coil pipe‘s float with high speed, the fouling will be deposited and adheres to the pipe’s outer wall difficultly during the operation process. At the same time, Even though there is a little fouling on the pipe’s outer wall, the fouling will break off automatically because the coil pipe will flex along with temperature change,therefore the traditional fouling-release technique is needless and the heat exchanger can keep the best work condition for long term. 3. The accurate temperature control The heat exchanger is collocated with the high-accuracy “intellectualized temperature adjuster”, it can inspect the water temperature continuously and automatically and will instruct the controlling valves to regulate the flowing quantity of the hot mediator in the coil pipe, the outlet water temperature will be kept in the scope of ±2°C of the set point in the case that the charge is waving. 4. Less floor space The exchanger has compact structure,so the floor space required is only 10 percent of the tubular heat exchanger that has the same function. The fabrication cost is reduced and space is utilized efficiently, it is also convenient for hoisting assembly and transportation.